|• Three-phase reactance for
rejection of harmonics.
• They avoid resonance between the inductive impedance (line, power transformer) and the three-phase capacitors used for
power factor correction.
• Tuned with capacitors
MA/C/CE TER RCT or DWCAP RCT, at resonance frequencies of 210, 189 Hz or 134 Hz (252, 227 and 160 Hz if the nominal frequency is 60 Hz).
|The technical department of RTR Energy offers the possibility of manufacturing
equipment according to the needs of customer application, defining power, voltage, frequency…
Dimensions and weight, consult.
|• Very low loss magnetic plate.
• Conductor with insulation H (180ºC), in permanent regime.
• Thermal protection.
• Specially designed windings
to increase ventilation and improve heat dissipation.
• Dry type vacuum varnished for ensure quiet operation and moisture resistant.
|• IEC 60831-1/2:2014
• UNE-EN 60831-1/2:2014
• UL 94. 20141031-E470994