|Under order||Materials and
|• Three-phase reactance for rejection
• They avoid resonance between the inductive impedance (line, power transformer) and the three-phase capacitors used for power factor correction.
• Tuned with capacitors MA/C/CE TER RCT or DWCAP RCT, at resonance frequencies of 210, 189 Hz or 134 Hz (252, 227 and 160 Hz if the nominal
frequency is 60 Hz).
|The technical department of RTR Energy offers the possibility of manufacturing equipment according to the needs of customer application, defining power, voltage, frequency…
Dimensions and weight, consult.
|• Very low loss magnetic plate.
• Aluminum conductor.
• Thermal protection.
• Specially designed windings to increase ventilation and improve heat
• Dry type vacuum varnished for ensure quiet operation and moisture resistance.
|• UNE-EN 60076-6
• IEC 60076-6
|Nominal Frequency||50Hz (60Hz on request)||Linearity||• 7% Linearity= 1,9 x In
• 14% Linearity= 1,7 x In
|Protection Thermostat||132° C|
|Overvoltage Factor||7%, 14% (Other frequencies
|Insulation Voltage||3kV||Thermal insulation||H (180ºC)|
|Tolerance (Inductance)||±5%||Maximum overload||1,1 x In||Degree of Protection||IP-00|